When you become our newest member, you’ll be joining more than 20,000 active Australian singles online, our proven matchmaking features allow you to meet Australian men and women, guys and girls from any town, city or state across Australia.
You’ll enjoy 24/7 unrestricted access to our live chat rooms services as well as browsing and connecting with singles via our vast pool of members.
I've read elsewhere on this forum the negatives associated with braided gas lines and how they are prone to stuffing up regulators etc. Queensland Petroleum and Gas Inspectorate Safety Alert No.
29 15 December 2006 Two-Stage Gas Regulator Failure What happened?
However, similar effects have been found with regulators connected to copper pigtails.
Almost all regulators found to exhibit these failures are the smallest available (around 200 MJ/hr) Recommendations Use regulators of capacity at least 300MJ/hr.
We encourage you to use Free Dating Australia to meet your next perfect match, or even a new friend.
We’ve designed the perfect platform to start your search now!Key issues Experiments by LPG Australia and the Department of Mines and Energy SIMTARS laboratory have demonstrated that some residue can be formed when LPG liquid is deposited in flexible hoses.They have demonstrated that some hoses can produce unacceptable amounts of residue which can then affect regulator performance if allowed to drain into the regulator.Use copper pigtails for fixed installations and low-loss flexible hose for mobile applications such as caravans (check with your hose supplier).Mount regulators above the level of the cylinder valve.Removed the line from under regulator gas present, undid joint under stove, no gas. Reg is down low so crap in the line is a distinct possibilty I suppose.